When I try to use the A-B Ethernet ActiveX Control with a 1761-NET-ENI module, I get result code 10061
1761-NET-ENI module uses a different wrapper protocol than direct PLC connection.
You must tell the ActiveX Control that you wish to communicate with the target device through a 1761-NET-ENI module.
Version 2.1 and higher: Add 'ENI:' to the NodeAddress property anywhere after the third field.
Version 2.0 and below: upgrade to current version, then follow these instructions.
To communicate with a MicroLogix through a 1761-NET-ENI module at IP address '192.168.0.61', set the NodeAddress property as follows:
Asabtcp1.NodeAddress = "192.168.0.11,,,ENI:"
Refer to Help > Properties > NodeAddress for complete details.